Your Key to Wireless Energy Management Systems
The Entuit Thermostat uses wireless communication to provide quick and easy implementation of the energy-saving HVAC controls. When the thermostat receives an "occupied" signal from any of Entuit's wireless switch or sensor, the user immediately gains full control of the HVAC settings. When the thermostat receives an "unoccupied" signal, it sets the room back to the preset unoccupied temperature. When used with Entuit's Gateway, the thermostat can also be connected to the LON or BACNet HVAC control systems.
The Guest does not have access to any internal menu operations therefore prohibiting the guest from altering any settings on the thermostat. This then eliminates the guest’s ability to tamper with the energy management system.
Real time clock.
Night-Time occupancy Set Back based on property’s pre-determined nightly time schedule.
(For example: If the occupancy override is enabled, and the time is set between 9:30pm and 7:00am, when the system detects occupancy one time, it will automatically stay in occupied mode for the duration of the time period. This advanced technology will prevent any false Set Backs during night time, and ultimately prevent any guest uncomfort or complaints.)
PRODUCT NUMBER: DESCRIPTION
ENIT 24V Wireless Thermostat
Range 50-150 feet (typical)
Frequency 315MHz / 868MHz / 902MHz
Input Voltage 24V
Max Loadings 24V (1.5amp/circuit)
Temperature Monitor Range 32°F to 99.9°F (0°C to 37.7°C)
Temperature Set Point Range 60°F to 85°F (15.5°C to 29.5°C)
Operating Temperatures 14° to 131° F (-10° to 55° C)
Storage Temperature -4° to 131° F ( -20° to 55° C)
Sampling Rate Every 5 seconds
Display format Liquid Crystal Display (LCD)
Fan Control Selectable: Auto Cycle, Low,
Medium, High, Economy, Off
Memory Stores up to 30 switch IDs
Accuracy + / - 1°F (0.5°C)
Heat / Cool Control 1 Heat and 1 Cool circuit;
Heat pump reversing valve circuit
Dimensions 3.5” x 5.0” x 1.5”
Radio Certiﬁcations FCC (U.S. SZV-TCM2XXC);
IC (Canada 5713A-TCM2XXC)
BIDIRECTIONAL DATA FLOW
Remotely Configure: Monitor
Edit set-points Temperature/Set-point
Configure Occupied/Unoccupied Humidity
Change Configuration Fan Status
Limit User Capabilities Compressor Status
ser™ Technology Valve Status
(Including relative and absolute Pipe Temperature
Fan Control Mode (heating / cooling)
© Copyright 2017 Entuit, Inc.
email - email@example.com